<?xml version="1.0" encoding="iso-8859-1"?>
<ISO15745Profile xmlns="http://www.profibus.com/GSDML/2003/11/DeviceProfile" xmlns:xsi="http://www.w3.org/2001/XMLSchema-instance" xsi:schemaLocation="http://www.profibus.com/GSDML/2003/11/DeviceProfile ..\xsd\GSDML-DeviceProfile-V2.3.xsd">
  <ProfileHeader>
    <ProfileIdentification>PROFINET Device Profile</ProfileIdentification>
    <ProfileRevision>1.00</ProfileRevision>
    <ProfileName>Device Profile for PROFINET Devices</ProfileName>
    <ProfileSource>PROFIBUS Nutzerorganisation e. V. (PNO)</ProfileSource>
    <ProfileClassID>Device</ProfileClassID>
    <ISO15745Reference>
      <ISO15745Part>4</ISO15745Part>
      <ISO15745Edition>1</ISO15745Edition>
      <ProfileTechnology>GSDML</ProfileTechnology>
    </ISO15745Reference>
  </ProfileHeader>
  <ProfileBody>
    <DeviceIdentity VendorID="0x024F" DeviceID="0x0570">
      <InfoText TextId="TOK_InfoText_DevIdent" />
      <VendorName Value="Elster GmbH" />
    </DeviceIdentity>
    <DeviceFunction>
      <Family MainFamily="General" ProductFamily="BCU/FCU5xx" />
    </DeviceFunction>
    <ApplicationProcess>
      <DeviceAccessPointList>
        <DeviceAccessPointItem ID="DAP 2" PhysicalSlots="0..9"  ModuleIdentNumber="0x10000000" MinDeviceInterval="512" ImplementationType="BCU500" DNS_CompatibleName="bcu-570" FixedInSlots="0" ObjectUUID_LocalIndex="1" NameOfStationNotTransferable="true" DeviceAccessSupported="true" PNIO_Version="V2.2" AddressAssignment="DCP;LOCAL">
          <ModuleInfo CategoryRef="CAT_BCU500">
            <Name TextId="TOK_Name_DAP2" />
            <InfoText TextId="TOK_ModInfo_InfoTextId_DAP2" />
            <VendorName Value="Elster GmbH" />
            <OrderNumber Value="BCU570" />
            <HardwareRelease Value="11" />
            <SoftwareRelease Value="V0.11.18" />
          </ModuleInfo>
          <SubslotList>
            <SubslotItem SubslotNumber="32768" TextId="TOK_Subslot_8000" />
            <SubslotItem SubslotNumber="32769" TextId="TOK_Subslot_8001" />
            <SubslotItem SubslotNumber="32770" TextId="TOK_Subslot_8002" />
          </SubslotList>
          <IOConfigData MaxInputLength="128" MaxOutputLength="128" />
          <UseableModules>
            <ModuleItemRef ModuleItemTarget="ID_Mod_EA" AllowedInSlots="1" FixedInSlots="1" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Flamesig" AllowedInSlots="2" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Status" AllowedInSlots="3" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Error" AllowedInSlots="4" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Remaining" AllowedInSlots="5" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_RemTCtime" AllowedInSlots="6" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoBusInput" AllowedInSlots="7" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoInput" AllowedInSlots="8" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoOutput" AllowedInSlots="9" />
          </UseableModules>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="DAP 2" SubmoduleIdentNumber="0x11000000">
              <IOData />
              <ModuleInfo>
                <Name TextId="TOK_Name_DAP2" />
                <InfoText TextId="TOK_ModInfo_InfoTextId_DAP2" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
          <SystemDefinedSubmoduleList>
            <InterfaceSubmoduleItem ID="IDS_2I" SupportedRT_Class="Class1" SupportedRT_Classes="RT_CLASS_1" SupportedProtocols="SNMP;LLDP" SupportedMibs="MIB2" NetworkComponentDiagnosisSupported="true" SubslotNumber="32768" TextId="TOK_DAP_InterfaceModule" SubmoduleIdentNumber="0x12000000">
              <ApplicationRelations>
                <TimingProperties SendClock="32" ReductionRatio="1 2 4 8 16 32 64 128 256 512" /> <!-- Basis Takt ist 1ms 16,32 und 64ms sind erlaubt -->
              </ApplicationRelations>
            </InterfaceSubmoduleItem>
      <!-- MAUTypes 16=100TXFD -->
            <PortSubmoduleItem ID="IDS_2P1" SubslotNumber="32769" TextId="TOK_Port1" SubmoduleIdentNumber="0x1300000" MAUTypes="16"/>
            <PortSubmoduleItem ID="IDS_2P2" SubslotNumber="32770" TextId="TOK_Port2" SubmoduleIdentNumber="0x1400000" MAUTypes="16"/>
          </SystemDefinedSubmoduleList>
          <Graphics>
            <GraphicItemRef Type="DeviceSymbol" GraphicItemTarget="ID_Graph_1" />
          </Graphics>
        </DeviceAccessPointItem>
        <DeviceAccessPointItem ID="DAP 4" PhysicalSlots="0..9"  ModuleIdentNumber="0x15000000" MinDeviceInterval="512" ImplementationType="BCU500" DNS_CompatibleName="fcu-5" FixedInSlots="0" ObjectUUID_LocalIndex="1" NameOfStationNotTransferable="true" DeviceAccessSupported="true" PNIO_Version="V2.2" AddressAssignment="DCP;LOCAL">
          <ModuleInfo CategoryRef="CAT_FCU500">
            <Name TextId="TOK_Name_DAP4" />
            <InfoText TextId="TOK_ModInfo_InfoTextId_DAP4" />
            <VendorName Value="Elster GmbH" />
            <OrderNumber Value="FCU500_505" />
            <HardwareRelease Value="11" />
            <SoftwareRelease Value="V0.11.18" />
          </ModuleInfo>
          <SubslotList>
            <SubslotItem SubslotNumber="32768" TextId="TOK_Subslot_8000" />
            <SubslotItem SubslotNumber="32769" TextId="TOK_Subslot_8001" />
            <SubslotItem SubslotNumber="32770" TextId="TOK_Subslot_8002" />
          </SubslotList>
          <IOConfigData MaxInputLength="128" MaxOutputLength="128" />
          <UseableModules>
            <ModuleItemRef ModuleItemTarget="ID_Mod_EA_FCU500_505" AllowedInSlots="1" FixedInSlots="1" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Status_FCU500_505" AllowedInSlots="2" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Error_FCU500_505" AllowedInSlots="3" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Remaining_FCU500_505" AllowedInSlots="4" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_RemTCtime_FCU500_505" AllowedInSlots="5" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoBusInput_FCU500_505" AllowedInSlots="6" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoInput_FCU500_505" AllowedInSlots="7" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoOutput_FCU500_505" AllowedInSlots="8" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_STW_STB_Themp_FCU500_505" AllowedInSlots="9" />
          </UseableModules>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="DAP 4" SubmoduleIdentNumber="0x15010000">
              <IOData />
              <ModuleInfo>
                <Name TextId="TOK_Name_DAP4" />
                <InfoText TextId="TOK_ModInfo_InfoTextId_DAP4" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
          <SystemDefinedSubmoduleList>
            <InterfaceSubmoduleItem ID="IDS_2I_1" SupportedRT_Class="Class1" SupportedRT_Classes="RT_CLASS_1" SupportedProtocols="SNMP;LLDP" SupportedMibs="MIB2" NetworkComponentDiagnosisSupported="true" SubslotNumber="32768" TextId="TOK_DAP_InterfaceModule" SubmoduleIdentNumber="0x15020000">
              <ApplicationRelations>
                <TimingProperties SendClock="32" ReductionRatio="1 2 4 8 16 32 64 128 256 512" /> <!-- Basis Takt ist 1ms 16,32 und 64ms sind erlaubt -->
              </ApplicationRelations>
            </InterfaceSubmoduleItem>
      <!-- MAUTypes 16=100TXFD -->
            <PortSubmoduleItem ID="IDS_2P3" SubslotNumber="32769" TextId="TOK_Port1" SubmoduleIdentNumber="0x15030000" MAUTypes="16"/>
            <PortSubmoduleItem ID="IDS_2P4" SubslotNumber="32770" TextId="TOK_Port2" SubmoduleIdentNumber="0x15040000" MAUTypes="16"/>
          </SystemDefinedSubmoduleList>
          <Graphics>
            <GraphicItemRef Type="DeviceSymbol" GraphicItemTarget="ID_Graph_1" />
          </Graphics>
        </DeviceAccessPointItem>
        <DeviceAccessPointItem ID="DAP 6" PhysicalSlots="0..10" ModuleIdentNumber="0x16000000" MinDeviceInterval="512" ImplementationType="BCU500" DNS_CompatibleName="bcu-5"   FixedInSlots="0" ObjectUUID_LocalIndex="1" NameOfStationNotTransferable="true" DeviceAccessSupported="true" PNIO_Version="V2.2" AddressAssignment="DCP;LOCAL">
          <ModuleInfo CategoryRef="CAT_BCU560">
            <Name TextId="TOK_Name_DAP6" />
            <InfoText TextId="TOK_ModInfo_InfoTextId_DAP6" />
            <VendorName Value="Elster GmbH" />
            <OrderNumber Value="BCU560_565_580" />
            <HardwareRelease Value="11" />
            <SoftwareRelease Value="V0.11.18" />
          </ModuleInfo>
          <SubslotList>
            <SubslotItem SubslotNumber="32768" TextId="TOK_Subslot_8000" />
            <SubslotItem SubslotNumber="32769" TextId="TOK_Subslot_8001" />
            <SubslotItem SubslotNumber="32770" TextId="TOK_Subslot_8002" />
          </SubslotList>
          <IOConfigData MaxInputLength="128" MaxOutputLength="128" />
          <UseableModules>
            <ModuleItemRef ModuleItemTarget="ID_Mod_EA_BCU560_565_580" AllowedInSlots="1" FixedInSlots="1" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Flamesig_ZB_BCU560_565_580" AllowedInSlots="2" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Flamesig_HB_BCU560_565_580" AllowedInSlots="3" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Status_BCU560_565_580" AllowedInSlots="4" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Error_BCU560_565_580" AllowedInSlots="5" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_Remaining_BCU560_565_580" AllowedInSlots="6" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_RemTCtime_BCU560_565_580" AllowedInSlots="7" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoBusInput_BCU560_565_580" AllowedInSlots="8" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoInput_BCU560_565_580" AllowedInSlots="9" />
            <ModuleItemRef ModuleItemTarget="ID_Mod_InfoOutput_BCU560_565_580" AllowedInSlots="10" />

          </UseableModules>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="DAP 6" SubmoduleIdentNumber="0x16010000">
              <IOData />
              <ModuleInfo>
                <Name TextId="TOK_Name_DAP6" />
                <InfoText TextId="TOK_ModInfo_InfoTextId_DAP6" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
          <SystemDefinedSubmoduleList>
            <InterfaceSubmoduleItem ID="IDS_2I_2" SupportedRT_Class="Class1" SupportedRT_Classes="RT_CLASS_1" SupportedProtocols="SNMP;LLDP" SupportedMibs="MIB2" NetworkComponentDiagnosisSupported="true" SubslotNumber="32768" TextId="TOK_DAP_InterfaceModule" SubmoduleIdentNumber="0x16020000">
              <ApplicationRelations>
                <TimingProperties SendClock="32" ReductionRatio="1 2 4 8 16 32 64 128 256 512" /> <!-- Basis Takt ist 1ms 16,32 und 64ms sind erlaubt -->
              </ApplicationRelations>
            </InterfaceSubmoduleItem>
      <!-- MAUTypes 16=100TXFD -->
            <PortSubmoduleItem ID="IDS_2P5" SubslotNumber="32769" TextId="TOK_Port1" SubmoduleIdentNumber="0x16030000" MAUTypes="16"/>
            <PortSubmoduleItem ID="IDS_2P6" SubslotNumber="32770" TextId="TOK_Port2" SubmoduleIdentNumber="0x16040000" MAUTypes="16"/>
          </SystemDefinedSubmoduleList>
          <Graphics>
            <GraphicItemRef Type="DeviceSymbol" GraphicItemTarget="ID_Graph_1" />
          </Graphics>
        </DeviceAccessPointItem>
      </DeviceAccessPointList>
      <ModuleList>
        <!--BCU 570-->
        <ModuleItem ID="ID_Mod_EA"            ModuleIdentNumber="0x00000001">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_EA" />
            <InfoText TextId="TOK_InfoText_Mod_EA" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="1" SubmoduleIdentNumber="0x00000101">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Input" Length="2" UseAsBits="true" />
                </Input>
                <Output>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Output" Length="1" UseAsBits="true" />
                </Output>
              </IOData>
              <RecordDataList>
                <ParameterRecordDataItem Index="4" Length="1" TransferSequence="0">
                  <Name TextId="TOK_AlarmConfig" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="0" DefaultValue="1" AllowedValues="0..1" TextId="TOK_AlarmConfig_DeviceError" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="1" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_MalfunctionShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="2" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_SafetyShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="3" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_Warning" />
                </ParameterRecordDataItem>
              </RecordDataList>
      <ModuleInfo>
        <Name TextId="TOK_Name_Mod_EA" />
        <InfoText TextId="TOK_InfoText_Mod_EA" />
      </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Flamesig"      ModuleIdentNumber="0x00000002">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_FlameSig" />
            <InfoText TextId="TOK_InfoText_Mod_FlameSig" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="2" SubmoduleIdentNumber="0x00000102">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_FlameSig_Input" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_FlameSig" />
                <InfoText TextId="TOK_InfoText_Mod_FlameSig" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Status"        ModuleIdentNumber="0x00000003">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Status" />
            <InfoText TextId="TOK_InfoText_Mod_Status" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="3" SubmoduleIdentNumber="0x00000103">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Status_Input" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Status" />
                <InfoText TextId="TOK_InfoText_Mod_Status" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Error"         ModuleIdentNumber="0x00000004">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Error" />
            <InfoText TextId="TOK_InfoText_Mod_Error" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="4" SubmoduleIdentNumber="0x00000104">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Error_Input" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Error" />
                <InfoText TextId="TOK_InfoText_Mod_Error" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Remaining"     ModuleIdentNumber="0x00000005">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Remaining" />
            <InfoText TextId="TOK_InfoText_Mod_Remaining" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="5" SubmoduleIdentNumber="0x00000105">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Remaining_Input" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Remaining" />
                <InfoText TextId="TOK_InfoText_Mod_Remaining" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_RemTCtime"     ModuleIdentNumber="0x00000006">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_RemTCtime" />
            <InfoText TextId="TOK_InfoText_Mod_RemTCtime" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="6" SubmoduleIdentNumber="0x00000106">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_RemTCtime_Input" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_RemTCtime" />
                <InfoText TextId="TOK_InfoText_Mod_RemTCtime" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoBusInput"  ModuleIdentNumber="0x00000007">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoBusInput" />
            <InfoText TextId="TOK_InfoText_Mod_InfoBusInput" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="7" SubmoduleIdentNumber="0x00000107">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoBusInput_Input" Length="1" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoBusInput" />
                <InfoText TextId="TOK_InfoText_Mod_InfoBusInput" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoInput"     ModuleIdentNumber="0x00000008">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoInput" />
            <InfoText TextId="TOK_InfoText_Mod_InfoInput" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="8" SubmoduleIdentNumber="0x00000108">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoInput_Input" Length="2" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoInput" />
                <InfoText TextId="TOK_InfoText_Mod_InfoInput" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoOutput"    ModuleIdentNumber="0x00000009">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoOutput" />
            <InfoText TextId="TOK_InfoText_Mod_InfoOutput" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="9" SubmoduleIdentNumber="0x00000109">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoOutput_Input" Length="2" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoOutput" />
                <InfoText TextId="TOK_InfoText_Mod_InfoOutput" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <!--FCU 500-->
        <ModuleItem ID="ID_Mod_EA_FCU500_505"             ModuleIdentNumber="0x00000201">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_EA_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_EA_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="10" SubmoduleIdentNumber="0x00000301">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Input_FCU500_505" Length="2" UseAsBits="true" />
                </Input>
                <Output>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Output_FCU500_505" Length="1" UseAsBits="true" />
                </Output>
              </IOData>
              <RecordDataList>
                <ParameterRecordDataItem Index="4" Length="1" TransferSequence="0">
                  <Name TextId="TOK_AlarmConfig" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="0" DefaultValue="1" AllowedValues="0..1" TextId="TOK_AlarmConfig_DeviceError" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="1" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_MalfunctionShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="2" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_SafetyShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="3" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_Warning" />
                </ParameterRecordDataItem>
              </RecordDataList>
      <ModuleInfo>
        <Name TextId="TOK_Name_Mod_EA" />
        <InfoText TextId="TOK_InfoText_Mod_EA" />
      </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Status_FCU500_505"         ModuleIdentNumber="0x00000202">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Status_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_Status_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="11" SubmoduleIdentNumber="0x00000302">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Status_Input_FCU500_505" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Status_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_Status_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Error_FCU500_505"          ModuleIdentNumber="0x00000203">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Error_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_Error_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="12" SubmoduleIdentNumber="0x00000303">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Error_Input_FCU500_505" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Error_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_Error_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Remaining_FCU500_505"      ModuleIdentNumber="0x00000204">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Remaining_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_Remaining_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="13" SubmoduleIdentNumber="0x00000304">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Remaining_Input_FCU500_505" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Remaining_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_Remaining_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_RemTCtime_FCU500_505"      ModuleIdentNumber="0x00000205">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_RemTCtime_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_RemTCtime_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="14" SubmoduleIdentNumber="0x00000305">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_RemTCtime_Input_FCU500_505" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_RemTCtime_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_RemTCtime_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoBusInput_FCU500_505"   ModuleIdentNumber="0x00000206">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoBusInput_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_InfoBusInput_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="15" SubmoduleIdentNumber="0x00000306">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoBusInput_Input_FCU500_505" Length="1" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoBusInput_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_InfoBusInput_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoInput_FCU500_505"      ModuleIdentNumber="0x00000207">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoInput_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_InfoInput_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="16" SubmoduleIdentNumber="0x00000307">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoInput_Input_FCU500_505" Length="3" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoInput_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_InfoInput_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoOutput_FCU500_505"     ModuleIdentNumber="0x00000208">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoOutput_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_InfoOutput_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="17" SubmoduleIdentNumber="0x00000308">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoOutput_Input_FCU500_505" Length="2" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoOutput_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_InfoOutput_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_STW_STB_Themp_FCU500_505"  ModuleIdentNumber="0x00000209">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_STW_STB_Themp_FCU500_505" />
            <InfoText TextId="TOK_InfoText_Mod_STW_STB_Themp_FCU500_505" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="18" SubmoduleIdentNumber="0x00000309">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_STW_STB_Themp_Input_FCU500_505" Length="5" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_STW_STB_Themp_FCU500_505" />
                <InfoText TextId="TOK_InfoText_Mod_STW_STB_Themp_FCU500_505" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <!--BCU 560 / 565 / 580-->
        <ModuleItem ID="ID_Mod_EA_BCU560_565_580"           ModuleIdentNumber="0x00000401">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_EA_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_EA_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="19" SubmoduleIdentNumber="0x00000501">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Input_BCU560_565_580" Length="3" UseAsBits="true" />
                </Input>
                <Output>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_EA_Output_BCU560_565_580" Length="1" UseAsBits="true" />
                </Output>
              </IOData>
              <RecordDataList>
                <ParameterRecordDataItem Index="4" Length="1" TransferSequence="0">
                  <Name TextId="TOK_AlarmConfig" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="0" DefaultValue="1" AllowedValues="0..1" TextId="TOK_AlarmConfig_DeviceError" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="1" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_MalfunctionShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="2" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_SafetyShutdown" />
                  <Ref ValueItemTarget="VAL_Report" DataType="BitArea" BitLength="1" ByteOffset="0" BitOffset="3" DefaultValue="0" AllowedValues="0..1" TextId="TOK_AlarmConfig_Warning" />
                </ParameterRecordDataItem>
              </RecordDataList>
      <ModuleInfo>
        <Name TextId="TOK_Name_Mod_EA_BCU560_565_580" />
        <InfoText TextId="TOK_InfoText_Mod_EA_BCU560_565_580" />
      </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Flamesig_ZB_BCU560_565_580"  ModuleIdentNumber="0x00000402">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_FlameSig_ZB_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_FlameSig_ZB_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="20" SubmoduleIdentNumber="0x00000502">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_FlameSig_ZB_Input_BCU560_565_580" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_FlameSig_ZB_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_FlameSig_ZB_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Flamesig_HB_BCU560_565_580"  ModuleIdentNumber="0x00000403">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_FlameSig_HB_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_FlameSig_HB_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="21" SubmoduleIdentNumber="0x00000503">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_FlameSig_HB_Input_BCU560_565_580" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_FlameSig_HB_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_FlameSig_HB_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Status_BCU560_565_580"       ModuleIdentNumber="0x00000404">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Status_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_Status_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="22" SubmoduleIdentNumber="0x00000504">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Status_Input_BCU560_565_580" Length="1" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Status_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_Status_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Error_BCU560_565_580"        ModuleIdentNumber="0x00000405">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Error_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_Error_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="23" SubmoduleIdentNumber="0x00000505">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Error_Input_BCU560_565_580" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Error_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_Error_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_Remaining_BCU560_565_580"    ModuleIdentNumber="0x00000406">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_Remaining_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_Remaining_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="24" SubmoduleIdentNumber="0x00000506">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_Remaining_Input_BCU560_565_580" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_Remaining_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_Remaining_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_RemTCtime_BCU560_565_580"    ModuleIdentNumber="0x00000407">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_RemTCtime_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_RemTCtime_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="25" SubmoduleIdentNumber="0x00000507">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_RemTCtime_Input_BCU560_565_580" Length="2" UseAsBits="false" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_RemTCtime_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_RemTCtime_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoBusInput_BCU560_565_580" ModuleIdentNumber="0x00000408">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoBusInput_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_InfoBusInput_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="26" SubmoduleIdentNumber="0x00000508">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoBusInput_Input_BCU560_565_580" Length="1" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoBusInput_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_InfoBusInput_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoInput_BCU560_565_580"    ModuleIdentNumber="0x00000409">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoInput_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_InfoInput_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="27" SubmoduleIdentNumber="0x00000509">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoInput_Input_BCU560_565_580" Length="3" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoInput_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_InfoInput_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
        <ModuleItem ID="ID_Mod_InfoOutput_BCU560_565_580"   ModuleIdentNumber="0x0000040A">
          <ModuleInfo>
            <Name TextId="TOK_Name_Mod_InfoOutput_BCU560_565_580" />
            <InfoText TextId="TOK_InfoText_Mod_InfoOutput_BCU560_565_580" />
          </ModuleInfo>
          <VirtualSubmoduleList>
            <VirtualSubmoduleItem ID="28" SubmoduleIdentNumber="0x0000050A">
              <IOData>
                <Input>
                  <DataItem DataType="OctetString" TextId="TOK_Mod_InfoOutput_Input_BCU560_565_580" Length="2" UseAsBits="true" />
                </Input>
              </IOData>
              <ModuleInfo>
                <Name TextId="TOK_Name_Mod_InfoOutput_BCU560_565_580" />
                <InfoText TextId="TOK_InfoText_Mod_InfoOutput_BCU560_565_580" />
              </ModuleInfo>
            </VirtualSubmoduleItem>
          </VirtualSubmoduleList>
        </ModuleItem>
      </ModuleList>
      <ValueList>
        <ValueItem ID="VAL_Report">
          <Assignments>
            <Assign Content="0" TextId="TOK_NoReport" />
            <Assign Content="1" TextId="TOK_Report" />
          </Assignments>
        </ValueItem>
      </ValueList>
      <ChannelDiagList>
        <ChannelDiagItem ErrorType="256">
          <Name TextId="TOK_Name_DeviceError" />
          <Help TextId="TOK_HelpName_DeviceError" />
        </ChannelDiagItem>
        <ChannelDiagItem ErrorType="257">
          <Name TextId="TOK_Name_MalfunctionShutdown" />
          <Help TextId="TOK_HelpName_MalfunctionShutdown" />
        </ChannelDiagItem>
        <ChannelDiagItem ErrorType="258">
          <Name TextId="TOK_Name_SafetyShutdown" />
          <Help TextId="TOK_HelpName_SafetyShutdown" />
        </ChannelDiagItem>
        <ChannelDiagItem ErrorType="259">
          <Name TextId="TOK_Name_Warning" />
          <Help TextId="TOK_HelpName_Warning" />
        </ChannelDiagItem>
      </ChannelDiagList>
      <GraphicsList>
        <GraphicItem ID="ID_Graph_1" GraphicFile="GSDML-024F-0570-BCU5xx_FCU5xx_V10" />
      </GraphicsList>
      <CategoryList>
        <CategoryItem ID="CAT_BCU500" TextId="TOK_CAT_BCU500" />
        <CategoryItem ID="CAT_FCU500" TextId="TOK_CAT_FCU500" />
        <CategoryItem ID="CAT_BCU560" TextId="TOK_CAT_BCU560" />
      </CategoryList>
      <ExternalTextList>
        <PrimaryLanguage>
          <!--english-->
          <Text TextId="TOK_InfoText_DevIdent" Value="Control unit BCU/FCU 500" />
          <!--DAP 1 - text -->
          <Text TextId="TOK_CAT_BCU500" Value="BCU57x" />
          <Text TextId="TOK_CAT_FCU500" Value="FCU5xx" />
          <Text TextId="TOK_CAT_BCU560" Value="BCU56x/58x" />

          <!--DAP  - text -->
          <Text TextId="TOK_Name_DAP2" Value="BCU570 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP2" Value="BCU570 PROFINET IO-Device V2.0" />
          <Text TextId="TOK_Name_DAP4" Value="FCU500/505 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP4" Value="FCU500/505 PROFINET IO-Device V2.0" />
          <Text TextId="TOK_Name_DAP6" Value="BCU560/565/580 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP6" Value="BCU560/565/580 PROFINET IO-Device V2.0" />
          <!--port name-->
          <Text TextId="TOK_DAP_InterfaceModule" Value="PN-IO" />
          <Text TextId="TOK_Port1" Value="port 1 - RJ45" />
          <Text TextId="TOK_Port2" Value="port 2 - RJ45" />
          <Text TextId="TOK_Subslot_8000" Value="X1" />
          <Text TextId="TOK_Subslot_8001" Value="X1 P1" />
          <Text TextId="TOK_Subslot_8002" Value="X1 P2" />

          <!--module name-->
            <!--BCU570-->
            <Text TextId="TOK_Name_Mod_EA" Value="Inputs and outputs" />
            <Text TextId="TOK_Name_Mod_FlameSig" Value="Flame signal" />
            <Text TextId="TOK_Name_Mod_Status" Value="Status message" />
            <Text TextId="TOK_Name_Mod_Error" Value="Fault and warning signals" />
            <Text TextId="TOK_Name_Mod_Remaining" Value="Remaining times" />
            <Text TextId="TOK_Name_Mod_RemTCtime" Value="Remaining time for tightness test" />
            <Text TextId="TOK_Name_Mod_InfoBusInput" Value="PLC output information" />
            <Text TextId="TOK_Name_Mod_InfoInput" Value="BCU input terminal information" />
            <Text TextId="TOK_Name_Mod_InfoOutput" Value="BCU outlet terminal information" />

            <Text TextId="TOK_InfoText_Mod_EA" Value="Bus input and output bits of the BCU" />
            <Text TextId="TOK_InfoText_Mod_FlameSig" Value="0 - 25.5 µA flame signal of the burner, divided into 255 steps" />
            <Text TextId="TOK_InfoText_Mod_Status" Value="Current status message of the BCU" />
            <Text TextId="TOK_InfoText_Mod_Error" Value="Current fault and warning signals of the BCU" />
            <Text TextId="TOK_InfoText_Mod_Remaining" Value="Remaining time of current program step (if available)" />
            <Text TextId="TOK_InfoText_Mod_RemTCtime" Value="Remaining time for tightness test" />
            <Text TextId="TOK_InfoText_Mod_InfoBusInput" Value="Current PLC output information from the PLC to the BCU" />
            <Text TextId="TOK_InfoText_Mod_InfoInput" Value="Current signal condition of the BCU input terminals" />
            <Text TextId="TOK_InfoText_Mod_InfoOutput" Value="Current signal condition of the BCU outlet terminals" />

            <!--FCU500-->
              <Text TextId="TOK_Name_Mod_EA_FCU500_505" Value="Inputs and outputs" />
              <Text TextId="TOK_Name_Mod_Status_FCU500_505" Value="Status message" />
              <Text TextId="TOK_Name_Mod_Error_FCU500_505" Value="Fault and warning signals" />
              <Text TextId="TOK_Name_Mod_Remaining_FCU500_505" Value="Remaining times" />
              <Text TextId="TOK_Name_Mod_RemTCtime_FCU500_505" Value="Remaining time for tightness test" />
              <Text TextId="TOK_Name_Mod_InfoBusInput_FCU500_505" Value="PLC output information" />
              <Text TextId="TOK_Name_Mod_InfoInput_FCU500_505" Value="FCU input terminal information" />
              <Text TextId="TOK_Name_Mod_InfoOutput_FCU500_505" Value="FCU outlet terminal information" />
              <Text TextId="TOK_Name_Mod_STW_STB_Themp_FCU500_505" Value="STM/STL temperature" />

              <Text TextId="TOK_InfoText_Mod_EA_FCU500_505" Value="Bus input and output bits of the FCU" />
              <Text TextId="TOK_InfoText_Mod_Status_FCU500_505" Value="Current status message of the FCU" />
              <Text TextId="TOK_InfoText_Mod_Error_FCU500_505" Value="Current fault and warning signals of the FCU" />
              <Text TextId="TOK_InfoText_Mod_Remaining_FCU500_505" Value="Remaining time of current program step (if available)" />
              <Text TextId="TOK_InfoText_Mod_RemTCtime_FCU500_505" Value="Remaining time for tightness test" />
              <Text TextId="TOK_InfoText_Mod_InfoBusInput_FCU500_505" Value="Current PLC output information from the PLC to the FCU" />
              <Text TextId="TOK_InfoText_Mod_InfoInput_FCU500_505" Value="Current signal condition of the FCU input terminals" />
              <Text TextId="TOK_InfoText_Mod_InfoOutput_FCU500_505" Value="Current signal condition of the FCU outlet terminals" />
              <Text TextId="TOK_InfoText_Mod_STW_STB_Themp_FCU500_505" Value="Temperature in Kelvin and status of the safety temperature limiter and safety temperature monitor (only available on device versions with temperature module)" />

            <!--BCU 560/65/80-->
              <Text TextId="TOK_Name_Mod_EA_BCU560_565_580" Value="Inputs and outputs" />
              <Text TextId="TOK_Name_Mod_FlameSig_ZB_BCU560_565_580" Value="Burner 1 flame signal" />
              <Text TextId="TOK_Name_Mod_FlameSig_HB_BCU560_565_580" Value="Burner 2 flame signal" />
              <Text TextId="TOK_Name_Mod_Status_BCU560_565_580" Value="Status message" />
              <Text TextId="TOK_Name_Mod_Error_BCU560_565_580" Value="Fault and warning signals" />
              <Text TextId="TOK_Name_Mod_Remaining_BCU560_565_580" Value="Remaining times" />
              <Text TextId="TOK_Name_Mod_RemTCtime_BCU560_565_580" Value="Remaining time for tightness test" />
              <Text TextId="TOK_Name_Mod_InfoBusInput_BCU560_565_580" Value="PLC output information" />
              <Text TextId="TOK_Name_Mod_InfoInput_BCU560_565_580" Value="BCU input terminal information" />
              <Text TextId="TOK_Name_Mod_InfoOutput_BCU560_565_580" Value="BCU outlet terminal information" />

              <Text TextId="TOK_InfoText_Mod_EA_BCU560_565_580" Value="Bus input and output bits of the BCU" />
              <Text TextId="TOK_InfoText_Mod_FlameSig_ZB_BCU560_565_580" Value="0 - 25.5 µA flame signal of the burner, divided into 255 steps" />
              <Text TextId="TOK_InfoText_Mod_FlameSig_HB_BCU560_565_580" Value="0 – 25.5 µA flame signal of the burner, divided into255 steps (only available on BCU 580)" />
              <Text TextId="TOK_InfoText_Mod_Status_BCU560_565_580" Value="Current status message of the BCU" />
              <Text TextId="TOK_InfoText_Mod_Error_BCU560_565_580" Value="Current fault and warning signals of the BCU" />
              <Text TextId="TOK_InfoText_Mod_Remaining_BCU560_565_580" Value="Remaining time of current program step (if available)" />
              <Text TextId="TOK_InfoText_Mod_RemTCtime_BCU560_565_580" Value="Remaining time for tightness test" />
              <Text TextId="TOK_InfoText_Mod_InfoBusInput_BCU560_565_580" Value="Current PLC output information from the PLC to the BCU" />
              <Text TextId="TOK_InfoText_Mod_InfoInput_BCU560_565_580" Value="Current signal condition of the BCU input terminals" />
              <Text TextId="TOK_InfoText_Mod_InfoOutput_BCU560_565_580" Value="Current signal condition of the BCU outlet terminals" />

          <!-- Module PD description -->
            <!-- BCU570 -->
            <Text TextId="TOK_Mod_EA_Input" Value="PLC inputs" />
            <Text TextId="TOK_Mod_EA_Output" Value="PLC outputs" />
            <Text TextId="TOK_Mod_FlameSig_Input" Value="Flame signal" />
            <Text TextId="TOK_Mod_Status_Input" Value="Status message" />
            <Text TextId="TOK_Mod_Error_Input" Value="Fault and warning signals" />
            <Text TextId="TOK_Mod_Remaining_Input" Value="Remaining times" />
            <Text TextId="TOK_Mod_RemTCtime_Input" Value="Remaining time for tightness test" />
            <Text TextId="TOK_Mod_InfoBusInput_Input" Value="PLC output information" />
            <Text TextId="TOK_Mod_InfoInput_Input" Value="BCU input terminal information" />
            <Text TextId="TOK_Mod_InfoOutput_Input" Value="BCU outlet terminal information" />
            <!-- FCU500 -->
            <Text TextId="TOK_Mod_EA_Input_FCU500_505" Value="PLC inputs" />
            <Text TextId="TOK_Mod_EA_Output_FCU500_505" Value="PLC outputs" />
            <Text TextId="TOK_Mod_Status_Input_FCU500_505" Value="Status message" />
            <Text TextId="TOK_Mod_Error_Input_FCU500_505" Value="Fault and warning signals" />
            <Text TextId="TOK_Mod_Remaining_Input_FCU500_505" Value="Remaining times" />
            <Text TextId="TOK_Mod_RemTCtime_Input_FCU500_505" Value="Remaining time for tightness test" />
            <Text TextId="TOK_Mod_InfoBusInput_Input_FCU500_505" Value="PLC output information" />
            <Text TextId="TOK_Mod_InfoInput_Input_FCU500_505" Value="FCU input terminal information" />
            <Text TextId="TOK_Mod_InfoOutput_Input_FCU500_505" Value="FCU outlet terminal information" />
            <Text TextId="TOK_Mod_STW_STB_Themp_Input_FCU500_505" Value="STM/STL temperature" />
            <!-- BCU560/65/85 -->
            <Text TextId="TOK_Mod_EA_Input_BCU560_565_580" Value="PLC inputs" />
            <Text TextId="TOK_Mod_EA_Output_BCU560_565_580" Value="PLC outputs" />
            <Text TextId="TOK_Mod_FlameSig_ZB_Input_BCU560_565_580" Value="Flame signal 1" />
            <Text TextId="TOK_Mod_FlameSig_HB_Input_BCU560_565_580" Value="Flame signal 2" />
            <Text TextId="TOK_Mod_Status_Input_BCU560_565_580" Value="Status message" />
            <Text TextId="TOK_Mod_Error_Input_BCU560_565_580" Value="Fault and warning signals" />
            <Text TextId="TOK_Mod_Remaining_Input_BCU560_565_580" Value="Remaining times" />
            <Text TextId="TOK_Mod_RemTCtime_Input_BCU560_565_580" Value="Remaining time for tightness test" />
            <Text TextId="TOK_Mod_InfoBusInput_Input_BCU560_565_580" Value="PLC output information" />
            <Text TextId="TOK_Mod_InfoInput_Input_BCU560_565_580" Value="BCU input terminal information" />
            <Text TextId="TOK_Mod_InfoOutput_Input_BCU560_565_580" Value="BCU outlet terminal information" />

          <!-- Alarm Config -->
          <Text TextId="TOK_AlarmConfig" Value="Alarm configuration" />
          <Text TextId="TOK_AlarmConfig_DeviceError" Value="System fault" />
          <Text TextId="TOK_AlarmConfig_MalfunctionShutdown" Value="Fault lock-out" />
          <Text TextId="TOK_AlarmConfig_SafetyShutdown" Value="Safety shut-down" />
          <Text TextId="TOK_AlarmConfig_Warning" Value="Warning" />
          <Text TextId="TOK_NoReport" Value="do not signal" />
          <Text TextId="TOK_Report" Value="signal" />

          <Text TextId="TOK_Name_DeviceError" Value="System fault" />
          <Text TextId="TOK_Name_MalfunctionShutdown" Value="Fault lock-out" />
          <Text TextId="TOK_Name_SafetyShutdown" Value="Safety shut-down" />
          <Text TextId="TOK_Name_Warning" Value="Warning" />
          <Text TextId="TOK_HelpName_DeviceError" Value="The control unit has performed a safety shut-down due to a system fault. (See Operating instructions, Assistance in the event of malfunction.)" />
          <Text TextId="TOK_HelpName_MalfunctionShutdown" Value="The control unit has performed a fault lock-out due to a process fault. (See Operating instructions, Assistance in the event of malfunction.)" />
          <Text TextId="TOK_HelpName_SafetyShutdown" Value="The control unit has performed a safety shut-down due to a process fault. (See Operating instructions, Assistance in the event of malfunction.)" />
          <Text TextId="TOK_HelpName_Warning" Value="The control unit signals a warning. (See Operating instructions, Assistance in the event of malfunction.)" />


      </PrimaryLanguage>
        <Language xml:lang="de">
          <Text TextId="TOK_InfoText_DevIdent" Value="Steuerung BCU/FCU 500" />
          <!--DAP 1 - text -->
          <Text TextId="TOK_CAT_BCU500" Value="BCU57x" />
          <Text TextId="TOK_CAT_FCU500" Value="FCU5xx" />
          <Text TextId="TOK_CAT_BCU560" Value="BCU56x/58x" />
          <!--DAP 2 - text -->
          <Text TextId="TOK_Name_DAP2" Value="BCU570 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP2" Value="BCU570 PROFINET IO-Device V2.0" />
          <Text TextId="TOK_Name_DAP4" Value="FCU500/505 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP4" Value="FCU500/505 PROFINET IO-Device V2.0" />
          <Text TextId="TOK_Name_DAP6" Value="BCU560/565/580 V2.0" />
          <Text TextId="TOK_ModInfo_InfoTextId_DAP6" Value="BCU560/565/580 PROFINET IO-Device V2.0" />
          <!--port name-->
          <Text TextId="TOK_DAP_InterfaceModule" Value="PN-IO" />
          <Text TextId="TOK_Port1" Value="port 1 - RJ45" />
          <Text TextId="TOK_Port2" Value="port 2 - RJ45" />
          <Text TextId="TOK_Subslot_8000" Value="X1" />
          <Text TextId="TOK_Subslot_8001" Value="X1 P1" />
          <Text TextId="TOK_Subslot_8002" Value="X1 P2" />

          <!--module name-->
            <!--BCU570-->
            <Text TextId="TOK_Name_Mod_EA" Value="Eingänge und Ausgänge" />
            <Text TextId="TOK_Name_Mod_FlameSig" Value="Flammensignal" />
            <Text TextId="TOK_Name_Mod_Status" Value="Statusmeldung" />
            <Text TextId="TOK_Name_Mod_Error" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Name_Mod_Remaining" Value="Restlaufzeiten" />
            <Text TextId="TOK_Name_Mod_RemTCtime" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Name_Mod_InfoBusInput" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Name_Mod_InfoInput" Value="Information Eingangsklemmen BCU" />
            <Text TextId="TOK_Name_Mod_InfoOutput" Value="Information Ausgangsklemmen BCU" />

            <Text TextId="TOK_InfoText_Mod_EA" Value="Bus Eingangs- und Ausgangsbits der BCU" />
            <Text TextId="TOK_InfoText_Mod_FlameSig" Value="Flammensignal 0 - 25,5 µA des Brenners in 255 Schritte unterteilt" />
            <Text TextId="TOK_InfoText_Mod_Status" Value="Aktuelle Statusmeldung der BCU" />
            <Text TextId="TOK_InfoText_Mod_Error" Value="Aktuelle Störmeldung und Warnmeldung der BCU" />
            <Text TextId="TOK_InfoText_Mod_Remaining" Value="Restlaufzeit des aktuellen Programmschritt (wenn verfügbar)" />
            <Text TextId="TOK_InfoText_Mod_RemTCtime" Value="Restlaufzeit der Dichtheitskontrolle" />
            <Text TextId="TOK_InfoText_Mod_InfoBusInput" Value="Aktuelle Ausgangsinformationen der SPS an die BCU von der SPS" />
            <Text TextId="TOK_InfoText_Mod_InfoInput" Value="Aktueller Signalzustand der BCU-Eingangsklemmen" />
            <Text TextId="TOK_InfoText_Mod_InfoOutput" Value="Aktueller Signalzustand der BCU-Ausgangsklemmen" />

            <!--FCU500-->
            <Text TextId="TOK_Name_Mod_EA_FCU500_505" Value="Eingänge und Ausgänge" />
            <Text TextId="TOK_Name_Mod_Status_FCU500_505" Value="Statusmeldung" />
            <Text TextId="TOK_Name_Mod_Error_FCU500_505" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Name_Mod_Remaining_FCU500_505" Value="Restlaufzeiten" />
            <Text TextId="TOK_Name_Mod_RemTCtime_FCU500_505" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Name_Mod_InfoBusInput_FCU500_505" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Name_Mod_InfoInput_FCU500_505" Value="Information Eingangsklemmen FCU" />
            <Text TextId="TOK_Name_Mod_InfoOutput_FCU500_505" Value="Information Ausgangsklemmen FCU" />
            <Text TextId="TOK_Name_Mod_STW_STB_Themp_FCU500_505" Value="STW/STB Temperatur" />

            <Text TextId="TOK_InfoText_Mod_EA_FCU500_505" Value="Bus Eingangs- und Ausgangsbits der FCU" />
            <Text TextId="TOK_InfoText_Mod_Status_FCU500_505" Value="Aktuelle Statusmeldung der FCU" />
            <Text TextId="TOK_InfoText_Mod_Error_FCU500_505" Value="Aktuelle Störmeldung und Warnmeldung der FCU" />
            <Text TextId="TOK_InfoText_Mod_Remaining_FCU500_505" Value="Restlaufzeit des aktuellen Programmschritt (wenn verfügbar)" />
            <Text TextId="TOK_InfoText_Mod_RemTCtime_FCU500_505" Value="Restlaufzeit der Dichtheitskontrolle" />
            <Text TextId="TOK_InfoText_Mod_InfoBusInput_FCU500_505" Value="Aktuelle Ausgangsinformationen der SPS an die FCU von der SPS" />
            <Text TextId="TOK_InfoText_Mod_InfoInput_FCU500_505" Value="Aktueller Signalzustand der FCU-Eingangsklemmen" />
            <Text TextId="TOK_InfoText_Mod_InfoOutput_FCU500_505" Value="Aktueller Signalzustand der FCU-Ausgangsklemmen" />
            <Text TextId="TOK_InfoText_Mod_STW_STB_Themp_FCU500_505" Value="Temperatur in Kelvin und Status des Sicherheitstemperaturbegrenzer und des Sicherheitstemperaturwächter. (Nur verfügbar bei Gerätevarianten mit Temperatur-Modul)" />

            <!--BCU560/65/80-->
            <Text TextId="TOK_Name_Mod_EA_BCU560_565_580" Value="Eingänge und Ausgänge" />
            <Text TextId="TOK_Name_Mod_FlameSig_ZB_BCU560_565_580" Value="Flammensignal Brenner 1" />
            <Text TextId="TOK_Name_Mod_FlameSig_HB_BCU560_565_580" Value="Flammensignal Brenner 2" />
            <Text TextId="TOK_Name_Mod_Status_BCU560_565_580" Value="Statusmeldung" />
            <Text TextId="TOK_Name_Mod_Error_BCU560_565_580" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Name_Mod_Remaining_BCU560_565_580" Value="Restlaufzeiten" />
            <Text TextId="TOK_Name_Mod_RemTCtime_BCU560_565_580" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Name_Mod_InfoBusInput_BCU560_565_580" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Name_Mod_InfoInput_BCU560_565_580" Value="Information Eingangsklemmen BCU" />
            <Text TextId="TOK_Name_Mod_InfoOutput_BCU560_565_580" Value="Information Ausgangsklemmen BCU" />

            <Text TextId="TOK_InfoText_Mod_EA_BCU560_565_580" Value="Bus Eingangs- und Ausgangsbits der BCU" />
            <Text TextId="TOK_InfoText_Mod_FlameSig_ZB_BCU560_565_580" Value="0 – 25,5 µA des Brenners in 255 Schritte unterteilt" />
            <Text TextId="TOK_InfoText_Mod_FlameSig_HB_BCU560_565_580" Value="0 - 25,5 µA des Brenners in 255 Schritte unterteilt (nur verfügbar bei BCU 580)" />
            <Text TextId="TOK_InfoText_Mod_Status_BCU560_565_580" Value="Aktuelle Statusmeldung der BCU" />
            <Text TextId="TOK_InfoText_Mod_Error_BCU560_565_580" Value="Aktuelle Störmeldung und Warnmeldung der BCU" />
            <Text TextId="TOK_InfoText_Mod_Remaining_BCU560_565_580" Value="Restlaufzeit des aktuellen Programmschritt (wenn verfügbar)" />
            <Text TextId="TOK_InfoText_Mod_RemTCtime_BCU560_565_580" Value="Restlaufzeit der Dichtheitskontrolle" />
            <Text TextId="TOK_InfoText_Mod_InfoBusInput_BCU560_565_580" Value="Aktuelle Ausgangsinformationen der SPS an die BCU von der SPS" />
            <Text TextId="TOK_InfoText_Mod_InfoInput_BCU560_565_580" Value="Aktueller Signalzustand der BCU-Eingangsklemmen" />
            <Text TextId="TOK_InfoText_Mod_InfoOutput_BCU560_565_580" Value="Aktueller Signalzustand der BCU-Ausgangsklemmen" />

          <!-- Module PD description -->
            <!--BCU570-->
            <Text TextId="TOK_Mod_EA_Input" Value="Eingänge SPS" />
            <Text TextId="TOK_Mod_EA_Output" Value="Ausgänge SPS" />
            <Text TextId="TOK_Mod_FlameSig_Input" Value="Flammensignal" />
            <Text TextId="TOK_Mod_Status_Input" Value="Statusmeldung" />
            <Text TextId="TOK_Mod_Error_Input" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Mod_Remaining_Input" Value="Restlaufzeiten" />
            <Text TextId="TOK_Mod_RemTCtime_Input" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Mod_InfoBusInput_Input" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Mod_InfoInput_Input" Value="Information Eingangsklemmen BCU" />
            <Text TextId="TOK_Mod_InfoOutput_Input" Value="Information Ausgangsklemmen BCU" />

            <!--FCU500/505-->
            <Text TextId="TOK_Mod_EA_Input_FCU500_505" Value="Eingänge SPS" />
            <Text TextId="TOK_Mod_EA_Output_FCU500_505" Value="Ausgänge SPS" />
            <Text TextId="TOK_Mod_Status_Input_FCU500_505" Value="Statusmeldung" />
            <Text TextId="TOK_Mod_Error_Input_FCU500_505" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Mod_Remaining_Input_FCU500_505" Value="Restlaufzeiten" />
            <Text TextId="TOK_Mod_RemTCtime_Input_FCU500_505" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Mod_InfoBusInput_Input_FCU500_505" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Mod_InfoInput_Input_FCU500_505" Value="Information Eingangsklemmen FCU" />
            <Text TextId="TOK_Mod_InfoOutput_Input_FCU500_505" Value="Information Ausgangsklemmen FCU" />
            <Text TextId="TOK_Mod_STW_STB_Themp_Input_FCU500_505" Value="STW/STB Temperatur" />

            <!--BCU560/565/580-->
            <Text TextId="TOK_Mod_EA_Input_BCU560_565_580" Value="Eingänge SPS" />
            <Text TextId="TOK_Mod_EA_Output_BCU560_565_580" Value="Ausgänge SPS" />
            <Text TextId="TOK_Mod_FlameSig_ZB_Input_BCU560_565_580" Value="Flammensignal 1" />
            <Text TextId="TOK_Mod_FlameSig_HB_Input_BCU560_565_580" Value="Flammensignal 2" />
            <Text TextId="TOK_Mod_Status_Input_BCU560_565_580" Value="Statusmeldung" />
            <Text TextId="TOK_Mod_Error_Input_BCU560_565_580" Value="Stör- und Warnmeldung" />
            <Text TextId="TOK_Mod_Remaining_Input_BCU560_565_580" Value="Restlaufzeiten" />
            <Text TextId="TOK_Mod_RemTCtime_Input_BCU560_565_580" Value="Restlaufzeit Dichtheitskontrolle" />
            <Text TextId="TOK_Mod_InfoBusInput_Input_BCU560_565_580" Value="Information Ausgänge SPS" />
            <Text TextId="TOK_Mod_InfoInput_Input_BCU560_565_580" Value="Information Eingangsklemmen BCU" />
            <Text TextId="TOK_Mod_InfoOutput_Input_BCU560_565_580" Value="Information Ausgangsklemmen BCU" />

          <!-- Alarm Config -->
          <Text TextId="TOK_AlarmConfig" Value="Alarm Konfiguration" />
          <Text TextId="TOK_AlarmConfig_DeviceError" Value="Systemfehler" />
          <Text TextId="TOK_AlarmConfig_MalfunctionShutdown" Value="Störabschaltung" />
          <Text TextId="TOK_AlarmConfig_SafetyShutdown" Value="Sicherheitsabschaltung" />
          <Text TextId="TOK_AlarmConfig_Warning" Value="Warnung" />
          <Text TextId="TOK_NoReport" Value="nicht melden" />
          <Text TextId="TOK_Report" Value="melden" />

          <Text TextId="TOK_Name_DeviceError" Value="Systemfehler" />
          <Text TextId="TOK_Name_MalfunctionShutdown" Value="Störabschaltung" />
          <Text TextId="TOK_Name_SafetyShutdown" Value="Sicherheitsabschaltung" />
          <Text TextId="TOK_Name_Warning" Value="Warnung" />
          <Text TextId="TOK_HelpName_DeviceError" Value="Die Steuerungseinheit hat eine Sicherheitsabschaltung auf Grund eines Systemfehlers durchgeführt. (Siehe Betriebsanleitung Hilfe bei Störungen)" />
          <Text TextId="TOK_HelpName_MalfunctionShutdown" Value="Die Steuerungseinheit hat eine Störabschaltung auf Grund eines Prozessfehlers durchgeführt. (Siehe Betriebsanleitung Hilfe bei Störungen)" />
          <Text TextId="TOK_HelpName_SafetyShutdown" Value="Die Steuerungseinheit hat eine Sicherheitsabschaltung auf Grund eines Prozessfehlers durchgeführt. (Siehe Betriebsanleitung Hilfe bei Störungen)" />
          <Text TextId="TOK_HelpName_Warning" Value="Die Steuerungseinheit signalisiert eine Warnung. (Siehe Betriebsanleitung Hilfe bei Störungen)" />

        </Language>
      </ExternalTextList>
    </ApplicationProcess>
  </ProfileBody>
</ISO15745Profile>